Installation instructions • Read online or download PDF • Rockwell Automation IF8 Compact IF8 Analog Input Module User Manual. Rockwell Automation IF8 Compact IF8 Analog Input Module User Manual – Download. Rockwell Automation IF8 Compact IF8 Analog. The Compact I/O modules can be used with a CompactLogix controller, IF4FXOF2F. IF8. IF16C. IF16V. IR6. IT6.
|Published (Last):||5 January 2016|
|PDF File Size:||19.49 Mb|
|ePub File Size:||16.48 Mb|
|Price:||Free* [*Free Regsitration Required]|
Input Data File Word For each input module, slot x, words in the input data file contain the analog values of the inputs. To allow communication between the controller and module, move the bus lever fully to the left 4 until it clicks.
However, some systems, like the ADN DeviceNet Adapter, also allow the bits to be altered as part of the control program, using communication rungs.
Wire fragments that fall into a module could cause damage at power up. Mounting screws are required on every module. NC Wiring for channels are identical.
Rockwell Automation IF8 Compact IF8 Analog Input Module User Manual | 32 pages
Tell us about it. Or point us to the URL where the manual is located.
You can use the bare wire mannual a spade lug. Replacing a Single Modu le within a System Host Controller Spacing for single-wide modules 35 mm 1. Overall hole spacing tolerance: Tell us what’s missing. The terminals will accept a 6. Remove the label from the door, mark the identification of each terminal with permanent ink, and slide the label back into the door. Approximate Shipping Weight with carton g 0.
What’s missing? Tell us about it.
Your markings ID tag will be visible when the module door is closed. Attach an end cap terminator 5 to the last module in the system by using the tongue-and-groove slots as before. The latches will momentarily open and lock into place. Loosen the terminal screws to be wired. Your manual failed to upload Don’t see a manual you are looking for? For More Inform ation The terminal screws are non-captive.
Ensure it is locked firmly in place. Lock the end cap bus terminator 6.
Route the wire under the terminal pressure plate. Channel 0 and 1 Configuration Data Channel 0 and 1 configuration data is shown below.
In that case, graphical screens are provided by the programmer to simplify configuration. This lets you individually cancel each low process alarm latch.
Rockwell Automation Support Rockwell Automation provides technical information on the web to assist mahual in using our products. The same information applies to all channels. Locate holes every Use a power supply that matches the input transmitter specifications.
Use M4 or 8 panhead screws.