Requirements of Bed material,Charcoal & Diesel. Bed material Maximum Particle size Bulk density Chemical composition MM TO The start up of fluidised bed combustion boilers has always been a subject of the most process of raising bed temperature above °C. In the process of. boilers/heaters is the concept of Fluidised Bed Combustion (FBC). A descriptive feature for Start up/ Firing Procedure for AFBC boiler/heater bed. Initially.
|Published (Last):||3 December 2007|
|PDF File Size:||15.88 Mb|
|ePub File Size:||18.77 Mb|
|Price:||Free* [*Free Regsitration Required]|
Bed material to be filled and level of defluidised bed should be MM of WC. Turn off the oil burners and remove from furnace. Ensure all personel were cleared.
Check the following valves are kept in open condition. Check the bed material and fludisation study is being done. Fuel feeders and controllers. Boiler light up procedure A fixed quantity of dry charcoal Kgs i.
Bed material Maximum Particle size Bulk density Chemical composition: Start the FD fan and maintain bed pressure mmwc. C and start the ash handling upp. Ensure all access doors are closed.
All interlocks to be cross checked. Afbc Boiler Operation Manual – boiler operation manual at Main steam stop and pilot valve. Afbc Boiler Operation Manual – ante-annum.
Keep the PA lines clear and take trial run procedjre feeder of first compartment. After stabilisation of bed temperatures stop the burners and LDO pumps.
Boiler Manual For Cfbc – boiler operation procedure? C and stable the boiler. Ensure feed water flow through economiser at the time of light up to avoid steaming of economiser. Valves before and after feed control valve in feed line. Start the Oight oil pump and maintain the oil pressure between 6.
Ensure the deaerator water level as normal. CFBC boiler operation procedure? Ensure all foreign materials are removed from furnance and pressure parts. Initally the top bed temperature will raise and at the time of mixing temperature drops and bottom temperature raises at the time of mixing.
AFBC ( Atmospheric Fluidized Bed Combustion ) BOILER COLD START UP PROCEDURE – ASKPOWERPLANT
Shiatsu Massage Manual Afbc boiler boiler, The Procedurw pump and drives. The pressure drop across bed is obtained for various air flow.
Maintain drum level at normal recommended level. Add gas plenum pressure P2 Furnace draught to P1.
Afbc Boiler Light Up Procedure
Measure air box pressure P1 MM of wc 3. Drum and main line vent. Inspect the boiler before start and check Manual on Boiler Tube Bhel steam generators products afbc boilers Tags: Cfbc boiler operation procedure? When the bed temperatures reaches Deg C start the drag chain coal feeder. Published on Oct View 3. Start up vent valve. Feed control valve and its bypass valve. Check for dry fuel MM is available in bunker and gates below bunker are open and fuel is available at feeder inlet.
Cethar Afbc Boiler Manual – dire searching for a ebook Cethar afbc boiler manual in A fixed quantity of diesel wetted Charcoal 40 Kgs is spread uniformly over the compartment.
Check the following equipments for adequate lubrication. Set the air flow to MM of wc P. Check the following valves in boiler are in closed condition. Bed super heater drains. Check instrument air pressure is available at the required pressure 7 to 7.
Procesure the boiler before start and check the following 1. Inspect the boiler before start and check Manual on Boiler Tube Fluidized bed combustion – wikipedia, the free encyclopedia Fluidized bed combustion FBC is a combustion technology used to burn solid fuels.
Valves on feed line connecting to feed pumps operation.