61F-GPN2 AC from OMRON >> Specification: Liquid Level Controller, 61F- GP-N2 Series, Conductive, Vac, W, 80 ms. Find great deals for Omron 61F-GP-N2 Processor/Controller. Shop with confidence on eBay!. The 61F-GP-N2-AC is a Conductive Level Controller for automatic water supply and drainage control. Compact plug-in controller for single or two-point.
|Published (Last):||25 May 2006|
|PDF File Size:||17.24 Mb|
|ePub File Size:||2.31 Mb|
|Price:||Free* [*Free Regsitration Required]|
When resistance to high pressure is required.
Indication of liquid buildup due to filter blockages. In sewage use, electrode holders must be installed 10 to 20 cm apart from one another. Doing so may possibly result in electric shock. Using the low-level probe allows a wide differential between switching a pump on and off, and can avoid excessive pump operation during tank emptying or filling. Standard electrodes are made of stainless steel and usable in purified water, sea water, sewage, acid except acetic acid, sulfuric acid, etc.
To convert grams into ounces, multiply by 0. After fixation, osmium staining, and dissection the The earth terminal must be grounded.
Usually, electrodes are used in a set of three: If the sufficient interval cannot be provided, employ a low-sensitivity type Floatless Level Controller.
61F-GP-N2 – OMRON Industrial Automation
Between electrode E2 and E3 Response time Operate: Long distance for wiring onron causes malfunctions because stray capacitance may influence operation, or abnormal surges or noise may run through electrode circuit s. Limitation on Liability; Etc. Further, in no event shall liability of Omron Companies exceed the individual price of the Product on which liability is asserted. Used for sewage, sea water, etc. Fully fit the electrode into the connecting nut attached to the electrode holder.
Product specifications and accessories may be changed at any time based on improvements and other omrom. However, a type having 1, mm length electrodes is available on request. All units are in millimeters unless otherwise indicated. E1 Electrodes are in actual contact with the liquid. When in doubt, special part numbers may be assigned to fix or establish key specifications 61c-gp-n2 your application. For low specific liquids. To convert millimeters into inches, multiply by 0.
The diagram shows the connections for water supply. Doing so can reduce some effects of noise.
61F-GP-N2 – OMRON Industrial Automation
If the screws are not tight, DIN rail ssocket sthe product and cable s may lead to come off. If this differential is not required, the low-level probe need not be connected. Mounting style Flange Insulator material Phenol resin Max.
Electrochem review part 1 Consider the following two reactions: In the interest of product improvement, specifications are subject to change without notice. A low voltage is applied between these probes and the earth probe or tank, if it is 61g-gp-n2 conductive.
The output relay in the controller is energized when the water level reaches the high-level probe and de-energized when the water level falls below it. In this case the relay does not de-energize until the water level falls below the low-level probe. It is our practice to change part numbers when published ratings or features are changed, or when significant construction changes are made.
Any advice, recommendations or information given orally or in writing, are not to be construed as an amendment or addition to the above warranty. This information by itself is not sufficient for a complete determination of the suitability of the Product in combination with the end product, machine, system, or other application or use. Return of any Products by Buyer must be approved in writing by Omron before shipment.
Omron 61F-GP-N2 Processor/Controller | eBay
Precautions for Safe Use 1. Special 3-pole holder of small size and light weight. However, some specifications of the Product may be changed without any notice.
Easy-to-replace separate versions facilitate maintenance of electrodes. Please read and understand this catalog before purchasing the products. For acids, alkalis and sea water, electrode holders may be as much as 1 meter apart to operate properly. The water provides a current between the earth probe and the high-level probe.
Omron disclaims all other warranties, express or implied. Omron Companies shall not be liable for the suitability or unsuitability or the results from the use of Products in combination with any electrical or electronic components, circuits, system assemblies or any other materials or substances or environments.
Doing so may occasionally result in minor or moderate injury due to electric shock. This is a temporal bone which had an implant electrode Ideal for soft drink vendors, etc.
Information presented by Omron Companies has been checked and is believed to be accurate; however, no responsibility is assumed for clerical, typographical or proofreading errors or omissions. Between electrode E1 and E3 Release resistance Approx.