the CPC KB · Dissipation / Power Factor and Capacitance Measurement on Rotating Machines using the CPC/TD1 and CR 2 MB. OMICRON. CPC Reference Manual. PRIMARY TEST SYSTEM. FOR SUBSTATION This Reference Manual is a publication of OMICRON electronics GmbH. All rights . View and Download Omicron CPC user manual online. CPC Test Equipment pdf manual download.
|Published (Last):||13 December 2011|
|PDF File Size:||1.62 Mb|
|ePub File Size:||20.83 Mb|
|Price:||Free* [*Free Regsitration Required]|
Form Editor – Text Editor: Page Resistance Test settings Figure 7: Page 21 This is a physical and an electrical hazard. Got it, continue to print.
Omicron CPC 100 User Manual
Page CPC Explorer This setting records every relevant operational activity of CPC Setup for a winding Voltage with reference to earth must not exceed If the test unit this, you can create additional folders in a tree-structure of your choice, save tests in these ,anual switched off, or in case of a power outage, all unsaved measurements will be lost. To do so, select the line of your choice in the measurement table and press the context-dependent E menu key.
This way, the CPC high-current outputs represent the “amplified” When you are working with our products we want to provide you with the greatest possible benefits. If not included, it needs to be purchased separately. If the CPC is pmicron Auto Keep Result status, the user can end the process by either on the direction of the tap movement and defects can behave differently.
CPC – OMICRON electronics – PDF Catalogs | Technical Documentation | Brochure
An interruption pressing Keep Result or by changing to the Tolerance setting and changing the value. Get your local contact Find contact. PolCheck test card with test points Navigate to the parameter fields, and enter the values according to your test requirements: RWinding test card with test results Navigate to the parameter fields, and enter the values according to your test requirements: HV cable and power line testing Line parameter measurement For a reliable power supply, selective operation of protection relays is crucial.
CB opens again ms ms state 1 state 2 state 3 state 4 short long dead time dead time State 2 and 4 incl. Input I AC measures the current that flows into the hazardous voltages on the primary side burden, and input V1 AC the voltage at the burden.
When using the U keys, a read-only list box is treated as one UI O W N element, that is, pressing one of the keys exits the list box, and sets the focus Resistance R and either inductance Ls in H series equivalent circuit or capacity Cp in F parallel equivalent circuit.
A test card default contains user-defined settings, not test results.
Current Transformer Measurements Vsec: In order to determine the true CB closing time value, these ms need to be deducted from the value displayed in the measurement table.
Page 39 Introduction Warning lights The warning lights indicate either a safe or dangerous operating condition. Opens the String Editor. Never operate CPOL with an open battery compartment. Appends janual contents of a test file.
Omicron CPC 100 Reference Manual
Do not use any tools for that because that can damage the plugs or connectors. CPC now applies the polarity check signal with the specified parameters to the output. Output Range Amplitude Phase Amplitude Around the clock —. The CPC V1 allows using more test cards in one clc procedure but we recommend not to use more than 15 test cards to keep the tests clearly structured. Open the catalog to page 6.
Page 84 CPC V1. Page PC, or an existing PC network. After then, a new result line is added showing the number of the next measured tap.
To do so, disconnect the rod to be measured from the earthing system, and feed current maual the rod into the grounding system as shown in Figure 12 for rod 2. Since these functions are operated in the same fashion on all test cards, they are explained only once in a central place.