Technical Rule – Code of Practice. DVGW G (A) |June Pressure testing methods for gas transmission/gas distribution. DVGW G – DVGW G Polyethylen gas pipelines with an operating pressure up to and including 10 bar (PE 80, PE and PE-Xa) -. Technical rule [WITHDRAWN] Article is not orderable. DVGW G Compression strength test for pipelines and facilities of gas supply.
|Published (Last):||27 February 2010|
|PDF File Size:||4.34 Mb|
|ePub File Size:||2.23 Mb|
|Price:||Free* [*Free Regsitration Required]|
Drucken Teilen Xing Twitter. For this reason it is advisable to 4699 out the pressure test over a period of at least 24 hours. The test sections must be defined so that:.
The pressure test must be carried out in compliance with the requirements laid down in the relevant rules and regulations, e. Water absorption in the cement-mortar pores may initially cause a drop in pressure even if the pipeline is completely watertight.
Before starting the test, the pipeline must be slowly and evenly filled with water at svgw rate of about 0.
Hydrostatic testing — CEPS a.s.
The test sections must be defined so that: Each pipeline must be subjected to a pressure test after it has been laid. The pressure must be brought back to the test level at regular intervals and in any case after a drop of 0. Vvgw pressure loss may amount to:.
To stabilize the pipeline section when the soil has finally settled and the dbgw lining has absorbed sufficient water. There are two basic test methods: Before the pressure test can be carried out, the pipeline must be covered with backfill material so as to avoid shifts in position, which could cause leaks.
The water loss method see DVGW Worksheet W can svgw used as an equivalent alternative to the pressure loss method described above.
Pressure test ǀ Mannesmann Line Pipe
Carry out as specified by the planner Main test: This applies in particular to pipelines with mechanical socket connections. The pressure loss may amount to: Determines the amount of air still in the pipeline. The main test is a test of the entire system, and in particular of the watertightness and proper execution and installation of the pipes, fittings, etc.
The joints need not be covered by backfill.
It is carried out over a period of 3 hours for pipes up to DN The pressure test is carried out in a maximum of three steps. The pipeline is to be tested over its entire length or, if necessary, in sections. Pressure tests must be carried out by qualified dvge with the relevant knowledge of pipeline engineering, the execution of pressure tests, the measurement techniques and the applicable safety regulations.