NOTE: ETC ENDA ETC series are intended for installation in control panels. Make sure that the device is used only for intended purpose. The shielding. Thank you for choosing ENDA EPC profile controller. * Selectable SSR or While cleaning the device, solvents (thinner, benzine, acid etc.) or corrosive. Double set point. Selectable sensor type (Pt, J, K, L, T, S, R). PID control function with accurate self-tuning. Digital inputs can be assigned to 3 different.
|Published (Last):||11 November 2004|
|PDF File Size:||17.14 Mb|
|ePub File Size:||8.81 Mb|
|Price:||Free* [*Free Regsitration Required]|
The value of parameter should be increased in interference. Use suitable compensation cables.
It’s eenda community-based project which helps to repair anything. Adjustable between 1 and seconds. The device must be protected against inadmissible humidity, vibrations, severe soiling and make sure that the operation temperature is not exceeded.
If self tune is achieved A. Read this document carefully before using this device. If 0 is selected, soft start feature will be enable and the device reaches set point value quickly.
Technical Specification |
Pay attention to the polarities of the thermocouple cables as shown in the figure right are connected to the. The shielding must be grounded on the instrument side.
Process value during normal operation Mnemonic parameter code during programming SV Display: The maximum value is the value of C.
Adjusable between 1 and If the selected input type is changed, the value of C. Adjustable between 0 and minutes.
Enda ETC Series PID Temperature Controllers Panel Mount
If band alarm is selected, A1. Adjustable between 1 and The normal value is 0.
If waited enough,the value increases at each step. During an installation, all of the cables that are connected to the device must be free of energy.
When self tune procedure begins with no failure, Pid. The same procedure is valid for the enxa key.
If 9240 key is pressed while P. Relative humidity According to EN Front panel: If this parameter is 1, digital filter runs enra quick. After PID is calculated A. Enter PID parameters of the system if they are known at the begining. If this parameter is adjusted to a value closer to the energy requirements of the system at the set point, process temperature is prevented to rise or drop to dangerous levels.
Selectable, and These cables should not be close to the power cables or components. S different from out1. If process value is Appropriate to begin self tune, rEdY. The installation and electrical connections must be carried on by a qualified staff and must be ebda to the relevant locally applicable regulations.
Before self tune procedure, A. Four kinds of functions can be selected. Therefore, when using a grounding thermocouple, do not connect the logic output terminals to the ground. Wnda Rated population degree Rear panel: If no key is pressed within 20 seconds during programming mode, the data is stored automatically and the run mode is entered.
The maximum value is the value of A1. RS Modbus communication None